*Coronavirus* - Back at work now, policy here
I get asked regularly by members of the public if Netaheats contains asbestos so there is clearly a lot of interest. The answer you will probably find disappointing and predictable. Some do, others don’t. There now, was that helpful? Thought not…
To comment meaningfully we need to find out which version of Netaheat you have. I suggest you check through the photos on my “Identify your Netaheat” page then come back here knowing your exact model.
Identifying asbestos can only be done with 100% reliability in a laboratory but to me, asbestos looks quite recognisable compared with the later (and safe) ceramic fibre seals. Asbestos seals are pale grey rather than white, and are clearly made of loose fibres prone to shedding when disturbed. Here is a series of photos of seals from various Netaheats, labelled according to what I think they are made from, in order to illustrate the subtle difference in appearance of each type of seal. I may however be wrong!
I rarely see these but from memory I think they all have friable asbestos seals around the removable front panel of the combustion chamber, and under the flue hood. These two seals need to be disturbed to carry out normal servicing. The boiler probably also was asbestos seals at the back, between the boiler backplate and the flue tube through the wall. This is just a guess though. I’m consequently reluctant to repair a Netaheat Mk1 in case the fault lies in the combustion chamber. If anyone needs to disturb the combustion chamber or flue hood seals, best to spray them with water from a plant sprayer to reduce the risk of any fibres being released into atmosphere. Better just replace the boiler in my opinion if you have one, as few parts are available to fix a Mk1 and due to the asbestos risk.
Similarly to the Mk1, I think all MkII Netaheats have asbestos seals on the flue hood and the combustion chamber front panel, so I prefer not to work on them unless the fault lies only in the controls box underneath, and the combustion chamber front panel does not need removing. If anyone here has a MkII with the more modern and safe glass fibre rope seals instead of asbestos, please get in touch and I’ll amend this page. Thanks!
This is the tricky one. I’d say 75% of the MkIIF Netaheats I see inside have modern safe glass rope seals, and 25% have asbestos. I’ve yet to figure out if there is a way of telling externally which MkIIF have asbestos so if you have a MkIIF, the best I can say is there is a significant chance yours does.
Probably no asbestos in any of these. I can’t say definitively but of the many hundreds (possibly thousands!) I’ve seen inside, I’ve yet to see an asbestos seal. This is no guarantee there are none out there anywhere though!
As above, I’ve never seen an asbestos seal inside a Netaheat Profile. Nor the later but identical, re-named version the “Potterton Profile”.
Hope all that helps….
If your boiler has broken down contact me for free help and advice by phone or text. I can arrange to visit and repair if necessary.
If you book a visit I shall wear a face covering (and gloves where practical), and observe social distancing.
Asbestos seals in this left hand column.
Ceramic fibre seals in this right hand column.
Copyright Michael Bryant 2020
Site first published 11th November 2010
Last updated 18th November 2020
Gas Safe Register 197499, CIPHE registration number 56207